The SX-2000SM System Manager is the master unit of TOA's Matrix System SX-2000 and can be mounted in an EIA Standard component rack (1-unit size). It controls the audio signal routing and priority control between the optional audio input units, audio output units and remote microphones of the SX-2000 Series. The SX-2000SM itself is equipped with 8 control inputs, 8 control outputs, failure status outputs, access indicators, mode indicators and failure indicators enabling a wide range of controls and status monitoring. The SX-2000SM supplies a regulated 24 VDC for external equipment. Up to 10,000 operations and failures of the entire system can be logged in the logbook. The SX-2000SM also features two monitored power inputs making possible the creation of a dual-redundant power system. Also the network connection is redundant. Equipped with two channels of interfaces for connecting to the emergency power supply units, power failures can be indicated and the system being put into a battery saving mode.
24 V DC (2 power inputs)
Aluminium, alumite process, black
482 x 44 x 333 mm (W x H x D)
CD (SX-2000 Setting Software, Setting Software instructions, Operation instructions) x 1, CF Card x 1, removable terminal plug (4 Pins) x 1, removable terminal plug (12 Pins) x 4, rack mounting screw with plain washer (5x12) x 4, screw Driver x 1, CF Card Adapter x 1, Installation Manual x 1, Please read this Manual first! x 1
System Manager, central control unit of the voice alarm system for installation in 19-inch cabinet racks (IEC 60297).
Separate ads for:
-Mode: emergency/standby/analog reserve way
-Activity LAN connection
-Activity of the audio and control network
-Errors: General/CPU/audio and control network
Separate buttons for:
-Acknowledgement of fault messages
-Resetting the fault signal
Acoustic warning in case of a malfunction in accordance with the relevant standards for voice alarm systems.
Redundant power supply for reliable power supply. Two network connections (100BaseTX) for redundant network for audio and control signals, additional analog reserve way. LAN connection to read the system activity, errors and operating conditions, as well as to set the system time. 8 Control inputs with opto-couplers and 8 control outputs with relay changeover contacts via pluggable connectors. Each input can be monitored either.
Two connectors for the monitoring of emergency equipment. Separate control outputs for the above mentioned error messages, E.g. to the forwarding and the BMZ.
The programming software included with the delivery.